By other listed materials and methods. Fireblocking or draftstopping is not required at the partition line in buildings equipped with an automatic sprinkler system installed throughout in accordance with Section The height of the parapet shall be not less than 30 inches mm above the point where the roof surface and the wall intersect. Where a smoke damper is installed within a duct, a smoke detector shall be installed inside the duct or outside the duct with sampling tubes protruding into the duct. Where the wall faces an unoccupied space. Substrates to receive SFRM shall be free of dirt, oil, grease, release agents, loose scale and any other condition that prevents adhesion. Shaft enclosures shall be constructed as fire barriers in accordance with Section or horizontal assemblies in accordance with Section , or both.
|Date Added:||27 January 2004|
|File Size:||69.21 Mb|
|Operating Systems:||Windows NT/2000/XP/2003/2003/7/8/10 MacOS 10/X|
|Price:||Free* [*Free Regsitration Required]|
Konica Minolta ineo – Logiciels – Konica Minolta
Where wood sleepers are used for laying wood flooring on masonry or concrete fire-resistance-rated floors, the space between the floor slab and the underside of the wood flooring shall be filled with an approved material to resist the free passage of flame gendric products of combustion or fireblocked in such a manner that there will be no open spaces under the flooring that will exceed square feet 9.
The aggregate width of openings at any floor level shall not exceed 25 percent of the genric of the wall. In Group I-2 and ambulatory care facilities, 166bw-1/2 sliding doors installed in accordance with Section Walls shall be permitted to terminate at the underside of noncombustible roof sheathing, deck or slabs where both buildings are provided with not less than a Class B roof covering.
The ceiling membrane of 1- and 2-hour fire-resistance-rated horizontal assemblies is permitted to be interrupted with the double wood top plate of a fire-resistance-rated wall assembly, provided that all penetrating items through the double top plates are protected in accordance with Section Fire barriers separating control areas shall have a fire-resistance rating of not less than that required in Section In other than Groups I-2 and I-3, a vertical opening that is not used as one of the applications listed in this section shall be permitted if the opening complies with all of the items below:.
The joint shall be sealed, treated or covered with an approved material or system to resist the free passage of flame and the products of combustion. Vertical openings contained entirely within a shaft enclosure complying with Section shall be permitted. Each opening through a fire wall shall be protected in accordance with Section As required by Table for exterior walls based on the fire separation distance.
The roof is covered with a minimum Class B roof covering, and.
Draftstopping is not required in buildings equipped throughout with an automatic sprinkler system in accordance with Section Where the fire-resistance rating determined in accordance with this exception exceeds the fire-resistance rating determined in accordance with ASTM E or ULthe fire exposure time period, water pressure and application duration criteria for the hose stream test of ASTM E or UL shall be based on the fire-resistance rating determined in accordance with this section.
A material shall not be classified as a noncombustible building construction material if it is subject to an increase in combustibility or flame spread beyond the limitations herein established through the effects of age, moisture or other atmospheric geneeric.
Two-hour fire-resistance-rated walls shall be permitted to terminate at the underside of 16nw-1/2 roof sheathing, deck or slab, provided: The annular space created by the penetration of an automatic sprinkler, provided it is covered by a metal escutcheon plate.
Smoke dampers are not required where the building is equipped throughout with an approved smoke control system in accordance with Section 16bd-1/2, and smoke dampers are not necessary for the operation and control of the system.
Insulation and coverings on or in 16bw-1/ penetrating item shall not penetrate the assembly unless the specific material used has been tested as part of the assembly in accordance with this section.
Unfaced fiberglass batt insulation used as fireblocking shall fill the entire cross section of the wall cavity to a minimum height of 16 inches mm measured vertically.
The required thickness and construction of fire-resistance-rated assemblies enclosing trusses shall be based on the results of full-scale tests or combinations of tests on truss components or on approved calculations based on such tests that satisfactorily demonstrate that the assembly has the required fire-resistance.
Joints made in or between smoke barriers shall comply with Section In Groups R-2 and R-3 where the entire building is provided with a Class C roof covering, the exterior wall shall be permitted to terminate at the underside of the roof sheathing or deck in Type III, IV and V construction, provided:. 16w-1/2 51 mm nominal lumber.
A total cumulative leakage of 50 cfm 0.
Generic 16bw 4 Twain Device Driver Download
Such isolation system protection applied to isolator units shall be suitably designed and securely installed so as not to dislodge, loosen, sustain damage or otherwise impair its ability to accommodate the seismic movements for which the isolator unit is designed and to maintain its integrity for the purpose of providing the required fire-resistance protection. Opening protectives are not required where the roof assembly of the adjacent building or structure has a fire-resistance rating of not less than 1 hour for a minimum distance of 10 feet mm from the exterior wall facing the imaginary line and the entire length and span of the supporting elements for the fire-resistance-rated roof assembly has a fire-resistance rating of not less than 1 hour.
Fire dampers for hazardous exhaust duct systems shall comply with the International Mechanical Code.
A material shall not be classified as a noncombustible building construction material if it is subject to an increase in combustibility or flame spread beyond the limitations herein established through the effects of age, moisture or other atmospheric conditions.
Fire and smoke dampers shall be provided with an approved means of access that is large enough to permit inspection and maintenance of the damper and its operating parts.
Generic 16BW-1/2 TWAIN Device driver free download for windows – VMware, – VMware Virtual Platform
Corrosion-resistant steel having a base metal thickness not less than 0. Fire assemblies that serve multiple purposes in a building shall comply with all of the requirements that are applicable for each of the individual fire assemblies. Incinerator rooms shall meet the provisions of Sections Where a horizontal assembly is required by other sections of this code, the assembly shall have a fire-resistance rating of not less than that required by that section.
Surface irregularities of SFRM shall be deemed acceptable. The fire-resistance rating of the fire barrier separating building areas from a shaft shall comply with Section Where a smoke damper is installed above smoke barrier doors in a smoke barrier, a spot-type detector shall be installed on either side of the smoke genericc door opening.